The Cause of Corrosion in Electrical Panel Boxes
A professional electrical contractor is necessary to fully evaluate and correct the condition. The contractor will definitely locate the source of moisture and make necessary repairs or replacements. More often the panel box and wiring is incredibly damaged and corroded, thus changing of the panel is require. Sometimes the panel box can be salvaged; at any cost the source of the moisture must be determined and solved in order to avoid worse effects.
So far the most typical cause of water intrusion in service enclosures and is associated together with the passage of an external service entry cable from outside, via the house wall, into buses which are situated in underground rooms or at a spot at the lower part in comparison with the factor of penetration of the electrical wires by means of the building wall.
Professional home maintenance inspectors offer a unique point of view on field failures: in accomplishing a comprehensive review of a building’s structures and materials, maintenance personnel may find typical external or interactive causes of damage or deterioration. In performing home inspection, one of the requirements is the uncovering of electrical panel box so the interior part of the panel can be inspected and viewed. The home inspector needs to inspect the internal electrical connections, breakers, grounding, wire type, wire size, box condition, wire condition, main breaker, and panel condition.
One of the most common mechanism through which wetness break into most of these enclosures is coming from roof/surface excess, inducing basement water intrusion and high internal dampness levels that in turn led to condensation.
Issues that may signify malfunction or hazardous conditions involve inconspicuous tarnish or corrosion on each component ; signs of overheated electric ground and balanced wiring at a corroded panel bus, and too hot electric branch outlet connecting lines which may or may not be due to a corroded circuit breaker that failed to catch, or more breakage at the connections of the service front wires, at wiring connections on outlet breaker fuses or specific fuse terminals, at neutral or ground bus bars or connections; or rust at the origin of electrical panel enclosure itself.
Water can travel down the interior of the coated electrical wire and then can enter the panel. The service wire will act like a sealed pipe bringing moisture into the panel box. If the electric meter is not tightly sealed on top where the service cable enters then it is more prone from leaks. Wind driven rain can also infiltrate a frayed or damaged main service cable and drip down to the panel box. A deteriorated lower service entrance wire will also contribute too the cause of moisture issues in the panel.
Detachment of the box cover of the electrical panel is needed when conducting a well performed home inspection. That way, the inspection in the panel interior will be easy but it must be done carefully. It is the responsibility of a New Jersey inspector to check internal connections, breakers, wire size, grounding, wire type, panel and box condition and of course, the main breaker. Rusting in the service panel is a common circumstance or problem that people usually encounter.
The qualified technicial will do all of these steps to accurately check and assess your electrical panels. If you find it difficult to find a reputable electrician from your yellow pages, you can find resources online.
Waldron Electric Heating and Cooling because we are leaders at everything electrical, far beyond figuring out electrical service determination for a building. Call Waldron Electric Heating & Cooling for the most reliable 24 hr service, and no complaints.
categories: aluminum cable wiring,heating and air,HVAC,electrical contractor,electricians,do it yourself,home repair,danger,safety,construction,family,house